Due to the request from the admin staff, we were required to install a new fax cable line at the admin office. The wire goes through from the ceiling of the admin office and reaches the connection point. The connection of the wire must do carefully as the wire is life.
In the evening, I and abang Fadzli checked the transducer in the power transformer as the reading of the measurement is out of range. After a round of checking, we found out that the problem is the transducer problem. A new transducer will be replaced when the ordered transducer reached. Other that involve is Mr. Tai, control and instrumental technician.